The suction tube is just biased and not in contact with the bottom, but reaches about 50 mm from it, this is to prevent suction positos, gels, etc. oxide plates, which eventually are deposited in the tank bottom.
The ability of the same, when constructed, is already taken into account this “loss” of volume.
The foam is slightly evaporable, if the tank is not full at all, said vapors just rusting tank wall, said oxidation is slow, because inside the tank is painted in epoxy, therefore and for greater longevity of the foam, in order to reduce as much as possible to the surface in contact with the atmosphere, an atmospheric tank containing foam is much better that it is always fully booked.
To prevent foam formation when filling , since otherwise , if the foam is poured freely by dropping a single orifice from a height a large amount of foam which would prevent filling in a single operation would occur on deposit . With the dip tube is achieved by filling the foam from the bottom , so that this problem does not occur.
- I give my consent to SABO to contact me in order to answer the questions raised through this form. I am aware that I can withdraw my consent at any time with future effects, by sending an e-mail to firstname.lastname@example.org
I am informed that the withdrawal of consent does not affect the legitimacy of the treatment based on the consent granted before the withdrawal of the same.
- Basic information about data protection
- Responsible SA DE PRODUCTOS QUÍMICOS BOTTAZZI ESPAÑOLA.
Purpose Management of the contact form.
Legitimation Consent of the interested party.
Recipients Data will not be transferred to third parties except to comply with legal obligations and for the proper exercise of the activity.
Rights Access, rectify and delete data, as well as other rights, as explained in the additional information.